IN THE USA
FUELMASTER IS ENGINEERED, MANUFACTURED AND
FACTORY ASSEMBLED IN THE UNITED STATES.
OFFERING TOTAL FUEL ACCOUNTING, EQUIPMENT
RELIABILITY AND UNEQUALED SUPPORT.
TOGETHER, WE WILL MASTER YOUR
800.888.9136 | MYFUELMASTER.com
such as gauge sticks and bailers, for operability
Owners and operators may conduct the operation
and maintenance walk-through inspections according
to a standard code of practice developed by a nationally
recognized association or independent testing
laboratory or according to requirements developed by
the implementing agency. EPA specifically included
PEI’s Recommended Practices for the Inspection and
Maintenance of UST Systems (PEI/RP900) as a code
of practice that may be used to meet the walk-through
Owners and operators who select the code of practice
option for meeting UST requirements must use the entire
code of practice. In other words, owners and operators will
not meet the walk-through inspection requirement if they
follow only some of the walk-through inspection areas in
the code of practice while ignoring others.
Other walk-through requirements include the following:
• Owners and operators must begin conducting walk-
through inspections three years after the effective date
of the new UST regulation.
• EPA will not change the cathodic protection
checks at the 60-day interval specified in the 1988